NEW ORLEANS - The company that supplied electricity to the Super Bowl says the blackout that halted the big game was caused by a device it installed specially to prevent a power failure.
But the utility stopped short of taking all the blame and said Friday that it was looking into whether the electrical relay at fault had a design flaw or a manufacturing defect.
The relay had been installed as part of a project begun in 2011 to upgrade the electrical system serving the Superdome in anticipation of the championship game. The equipment was supposed to guard against problems in the cable that links the power grid with lines that go into the stadium.
"The purpose of it was to provide a newer, more advanced type of protection for the Superdome," Dennis Dawsey, an executive with Entergy Corp., told members of the City Council. Entergy is the parent company of Entergy New Orleans, the city's main electric utility.
Entergy officials said the relay functioned with no problems during January's Sugar Bowl and other earlier events. It has been removed and will be replaced.
All systems at the Superdome are now working, and the stadium was to host a major Mardi Gras event Saturday night, said Doug Thornton, an executive with SMG, the company that manages the stadium for the state.
The relay was installed in a building near the stadium known as "the vault," which receives a line directly from a nearby Entergy substation. Once the line reaches the vault, it splits into two cables that go into the Superdome.
Sunday's power failure cut lights to about half of the stadium, halting play between the Baltimore Ravens and San Francisco 49ers and interrupting the nation's most-watched sporting event for 34 minutes.
Not long after the announcement, the manufacturer of the relay, Chicago-based S&C Electric Co., released a statement saying that the blackout occurred because system operators had put the relay's so-called trip setting too low to allow the device to handle the incoming electric load.
The equipment was owned and installed by Entergy New Orleans.
"If higher settings had been applied, the equipment would not have disconnected the power," said Michael J.S. Edmonds, vice president of strategic solutions for S&C.
In a follow-up statement, Entergy said that tests conducted by S&C and Entergy on the two relays at the Superdome showed that one worked as expected, the other did not.
Entergy spokesman Mike Burns said both relays had the same trip setting.
Entergy's announcement came shortly before company officials went before a committee of the City Council, which is the regulatory body for the company.
During the committee hearing, council member Susan Guidry asked Entergy executives whether they were "fairly certain" that the relay was faulty.
"That is correct," Dawsey said.
However, when asked if the outage was caused by the design or a defect in a part of the equipment, Entergy New Orleans CEO Charles Rice said that had not been determined.
"The equipment did not function properly," Rice said. "At this particular time, based upon our analysis, we cannot say definitively that there was a defect in design. What we do know is that the equipment for some unknown reason, at this particular time, did not react the way that it should have."
|NY Mets||6||Bottom 7th Inning|
|Philadelphia||1||Bottom 8th Inning|
|Miami||3||Top 9th Inning|
|Boston||6||Bottom 8th Inning|
|Minnesota||1||Bottom 8th Inning|
|NY Yankees||2||Top 9th Inning|
|Toronto||2||Bottom 9th Inning|
|Los Angeles||3:05 PM|
|San Francisco||3:05 PM|
|San Antonio||7:00 PM|
|New Jersey||6:00 PM|
|NY Rangers||6:00 PM|
|Grambling St||73||2nd Half 3:07|
|NC A&T||3:00 PM|
|Mount St Marys||6:00 PM|
|Delaware State||8:00 PM|
|Miss Valley St||8:00 PM|
|IUPU-Ft Wayne||8:00 PM|
|North Dakota St|
|TX-San Antonio||9:30 PM|
|Denver||56||2nd Half 7:34|
|Utah State||23||1st Half 4:42|
|Alabama A&M||5:30 PM|
|Fla Gulf Coast|
|East Tenn St||6:00 PM|
|Kennesaw St||6:00 PM|
|Louisiana Tech||6:00 PM|
|St Johns||8:00 PM|
|UC Santa Barbara||8:00 PM|
|TX-San Antonio||8:30 PM|
|Cal State Fullerton||10:30 PM|
|Long Beach St|
|San Diego State||10:30 PM|
|Aug 9 - vs. Houston||7 pm||X||27-13|
|Aug 16 - at Buffalo||6 pm||X||20-16|
|Aug 25 - at San Francisco||7 pm||X||34-14|
|Aug 29 - vs. Tennessee||7 pm||X||24-23|
|2013 regular season|
|Sep 8 - at Detroit||Noon||X||34-24|
|Sep 15 - at Chicago||Noon||X||31-30|
|Sep 22 - vs. Cleveland||Noon||X||31-27|
|Sep 29 - vs. Pittsburgh (in London)||Noon||X||34-27|
|Oct 6 - Bye|
|Oct 13 - vs. Carolina||Noon||X||35-10|
|Oct 21 - at. NY Giants||7:40 pm||X||23-7|
|Oct 27 - vs. Green Bay||7:30 pm||X||44-31|
|Nov 3 - at Dallas||Noon||X||27-23|
|Nov 7 - vs. Washington||7:25 pm||X||34-27|
|Nov 17 - at Seattle||3:25 pm||X||41-20|
|Nov. 24 - at Green Bay||Noon||26-26|
|Dec 1 - vs. Chicago||Noon||X||23-20|
|Dec 8 - at Baltimore||Noon||X||29-26|
|Dec 15 - vs. Philadelphia||Noon||X||48-30|
|Dec 22 - at Cincinnati||Noon||X||42-14|
|Dec 29 - vs. Detroit||Noon||X||14-13|
Poll: Which free-agent quarterback would you most like the Vikings to sign?