So You Want To Put A Chandelier Above Your Bath Tub...
April 3, 2012 — 5:18am
Chandeliers above bath tubs are apparently all the rage today. A few weeks ago I somehow ended up inspecting three houses in a row that had chandeliers installed above the bath tubs - one in Chaska, one in Saint Paul, and one in Victoria. They all look great, don't they?
Shortly after I posted these photos on the Structure Tech Facebook Page, Debbie Nelson said she's been seeing this trend for the last five years or so. She even gave me a couple links to web sites promoting this look - houzz from almost a year ago, and HGTV from about five years ago.
I think this is a great look, but as a home inspector I'm going to be a wet rag and say these are all improper installations. The diagram below comes from Code Check Electrical 6th Edition. This book is based on the 2011 National Electric Code (NEC), which prohibits any part of a chandelier from being within the shaded region shown below. This comes from section 410.10(D) of the NEC. The idea is that you're not supposed to be able to stand in a wet tub and change a light bulb at the same time.
This doesn't mean you shouldn't install a chandelier above your bath tub... but you're supposed to have a very tall ceiling to do it, and even then, the light should be rated for a wet or damp location. The image below shows a chandelier rated for a damp location - you'll notice that the bulbs are completely enclosed.
Reuben Saltzman is a second-generation home inspector with a passion for his work. Naturally, this blog is all about home inspections and home-related topics in the Twin Cities metro area. In addition to working at Structure Tech, he is also a licensed Truth-In-Sale of Housing Evaluator in Minneapolis, Saint Paul and several other cities.
FLIR has a relatively new pocket-sized infrared camera with all of the bells and whistles of the much larger and expensive E6. It boasts the same resolution as the E6 but it's a fraction of the price at only $699. With these features and benefits, this camera ought to put the E6 out to pasture.
I recently had an informative email exchange with a past client that highlighted the discovery of some especially nasty water damage behind the stone siding at her townhome. I was curious about the events that led up to the discovery, and it all came down to one person being very curious and very persistent. I thought she had such a great story to share that I invited her onto our podcast, which you can listen to below.
Stone siding might be the most problematic siding that we come across as home inspectors. This stuff is failing left and right all over the country, and most of time the homeowner has no idea when their wall is a rotted mess behind the siding.
Take a look around any room full of home inspectors, and you'll notice we look a lot alike. We are almost all white men with a lot of gray hair. It's as if there's an unwritten rule that you have to be an old white guy to be a home inspector.